Gas Fireplace, Gas Logs Service Everett, Washington
C.M. Heating offers full repair and maintenance services for hearth products in Everett, WA. If you have a dv gas fireplace, fireplace insert, gas stove, or gas logs, our service technicians have the experience to keep your system operating safely and at peak efficiency.
C.M. Heating stocks the parts and has the experience necessary to keep your gas fired fireplace or stove running properly.
Gas Fireplace Diagnostic Uninstall and reinstall fireplace to repair gas line
9th Ave W EVERETT, WA
Gas Fireplace Diagnostic Lopi ALLEGIANCE found unit with pilot off, relit pilot, tested components, test fired unit, working prpoperly. JL
124th st SE EVERETT, WA
Gas Fireplace Diagnostic Enviro SIE33 reset lockout, unit working properly.
Lombard Ave EVERETT, WA
Gas Fireplace Diagnostic Heatilator 6000GDV found switch under unit in the on position, conflicting with wall swich, turned off switch under unit, working properly. JL
112th st SW EVERETT, WA
Gas Fireplace Diagnostic HEATILATOR 6000GDV found switch under unit in the on position, conflicting with wall swich, turned off switch under unit, working properly. JL
112th ST SW EVERETT, WA
Gas Fireplace Diagnostic Clayton 40G fan no operation removed were from fan housing that was stopping fan. Unit working properly
105th PL SE EVERETT, WA
Gas Fireplace Diagnostic HEAT N GLO GRAND-I35C Several complaints with fireplace. Customer not happy with how surround looks, the way the fan sounds and how she cant feel it throughout the room, and not happy with the water vapor and fog that develops on the glass.. reported fan issue, test fired unit checked fan for proper operation, no apparent problems, unit and fan working properly. JL
Hoyt Ave EVERETT, WA
Gas Fireplace Diagnostic HEAT N GLO 6000GDV found loose appliance connector, tightened fittings, no leaks found.
12th AVE W EVERETT, WA
Gas Fireplace Diagnostic HEATILATOR GNDC30 ROBERT SHAW GAS VALVE/UNIVERSAL THERMOPILE & THERMOCOUPLE
37th ST EVERETT, WA
Gas Fireplace Diagnostic NAPOLEON GDS50-N found pilot lifting off thermocouple, added a pilot shield tested unit, working properly at this time, no other repairs available for this issue
90th ST SW EVERETT, WA
Gas Fireplace Diagnostic HEATILATOR GNDC30 found gas valve needs replacement faulty connection in valve.
90th ST SW EVERETT, WA
Gas Fireplace Diagnostic install glass right side up and put trim on correctly. JL
41st PL EVERETT, WA
Gas Fireplace Diagnostic FMI DVF36 found unit to have intermittent outings, wiring to valve relocated to stop outings, unit working properly at this time.
32nd DR SE EVERETT, WA
Gas Fireplace Diagnostic travis industries DVS Z/C removal and installation
East Grand Ave EVERETT, WA
Gas Furnace Diagnostic RHEEM RGRA-09EZAJS Found CO levels @ 450ppm and above from exhaust. Found combustion air mixing thru eccentric kit. Need to move cumbustion or intake pipe or replace kit. Cut intake pipe at furnace and now drawing combustion air from 1500ft2 basement. Advised customer to turn unit off if using any chemicals in the basement. Will call back with pricing and availibility.
Cascadia AVE EVERETT, WA
Gas Fireplace Diagnostic Lennox EDVI25 Found wire off of temp sensor, re-connected wire, tested unit, working properly.
Grand Ave EVERETT, WA
Gas Fireplace Diagnostic Dovre DV400S Found fireplace sooting inside. Vent pipe also sooting. Diagnostic findings, no natural gas orifice in burner. Customer had orifice and installed it. Fireplace running good now.
Walnut St EVERETT, WA
Gas Fireplace Maintenance Majestic 36DV89 Tested and inspected gas valve and pilot assembly. All operations normal. Inspected and cleaned glass, log set and pilot assembly. OK
45th Ave SE EVERETT, WA
Gas Fireplace Diagnostic Country I30 Found wiring to switch arcing to make switch react randomly.
Colby Ave EVERETT, WA
Gas Fireplace Diagnostic Regency U37-NG Found thermopile failing, replaced and fireplace running good at this time.
Cedar ST EVERETT, WA