No Heat in Arlington, Washington
Furnaces can be intimidating especially when they're not working. However there might be a silver lining to this stressful situation: roughly a quarter of all service calls can be resolved with easy fixes that are simple and inexpensive.
At C.M. Heating we help homeowners like you in Arlington, WA all the time with their heating systems. From simply offering advise, to complete system replacement, we have the knowledge and experience to help you resolve the challenges your heating system is presenting in the best possible way.
CM Heating went out to perform a furnace diagnostic and found Gas furnace failed to properly start on arrival. Two tries it start correctly.
Check safety limit devices, system components, co2 exhaust venting, gas lines, combustion control parts.
Cleaned filter, vacuumed dust and carbon dust from inside housing. Checked system sensors, co2 levels, and took measurements of consumable components.
1. No gas drip leg installed.
2. Flex gas line entering furnace housing.
3. 4in vent piping reduce to 3in at Y coupling
4. Igniter is reaching max limit of design specification.