Heat Pump Service Arlington, Washington
C.M. Heating services all types air conditioners or heat pumps in Arlington, WA. Our service technicians can diagnosis and repair your packaged or split systems in Arlington, WA and get your HVAC system back up to speed promptly.
Let us help you decide how best to solve you comfort and efficiency challenges quickly. If repair is the best choice, C.M. Heating stocks the parts you need. If you need to update your AC or Heat Pump system in Arlington, WA, we install a range of replacement systems.
CM Heating performed Maintenance on heat pump. Tested capacitor and contactor. Took amp draws of compressor and fan. Tested defrost. Checked delta t in heating
Heat pump is running properly at this time
Disconnect to the heat pump is not mounted properly
CM Heating completed service on both heat pump and furnace. I found no issues to note at this time. Both systems are running within the factory specs. Filter is still in good shape.
CM Heating Performed a maintenance service on both the heat pump and gas furnace. Check and verified individual system components. Took measurements to compare to manufacturer specifications or tolerances.
Changed out dirty 16x20x4 filter.
All operations normal at this time.
CM Heating completed Maintenance on furnace. Checked burners and flame sensor. Tested igniter. Took amp draws of motors. Visually inspected the control board and blower assembly. Changed filter and checked delta t. Cleared condensate line.
Furnace is running properly at this time
Maintenance on heat pump. Took amp draws of compressor and fan. Tested capacitor, hard start kit, and defrost board functionality. Took delta t. Visually inspected the outdoor coil is still clean.
Compressor amperage is good: 12.63 start 8.4 run amps
System is running properly at this time
Recommended adding surge protection to the outdoor unit
CM Heating Performed maintenance on a gas furnace, HP system. Recommended replacing components showing signs of wear/failing. Customer declined repair at this time. System is currently operational with no issues.
CM Heating went out for a heat pump diagnostic and found Heat exchangers are bad in furnace. I could not find direct reason for heat exchanger failure. Heat exchangers will need to be ordered. Customer to be quoted cost of replacement if issues are not related to install of equipment.