CM Heating Completed a fireplace diagnostic, found the pilot hood was clogged causing the flame to fall short of the flame sensor in turn causing the main burner to not light. Cleaned out pilot assembly and unit is now functioning properly. No concerns at this time.
CM Heating Completed fireplace diagnostic, unfortunately the fireplace worked every time I turned it on, however due to the age I would venture to guess it's a
CM Heating performed a fireplace diagnostic and found Pilot light had to be adjusted for flame to hit pilot assembly components. I cleaned thermocouple as it had soot on it from declining pilot flame. Mili volt reading is still slightly low on thermopile. Still at the bottom end of manufactures specs. Pilot was re lit, and fireplace was tested with no issues. I would recommend pilot assembly replacement if issue continues.
CM Heating Completed fireplace diagnostic, found gasket is deteriorating and there is rust throughout the firebox. Due to the age and condition of the unit, I recommend replacement of entire fireplace over any major repairs.
Referring all zero clearance consultations to
CM Heating Completed fireplace diagnostic. Re-lit pilot and discovered the thermopile had failed and was not sensing the flame from the pilot causing the main burner to fail ignition. Replaced thermopile and tested, fireplace now working properly. No other concerns at this time.
CM Heating Performed a gas fireplace maintenance today. Check gas components, cleaned glass, removed build up of dust, and added new embers. Put new batteries in receiver.
All operations normal at this time.