Furnace Cleaning Edmonds, Washington
Keeping your heating system in Edmonds, WA in good working order working requires scheduled maintenance. All equipment manufacturers suggest at least annual system cleaning and preventative maintenance. Our heating service technicians have years of experience working on furnaces like yours in Edmonds, WA. C.M. Heating service vehicles are on call and are fully equipped with the tools and parts necessary to keep your hot air furnace in good working order.
Our furnace repair, furnace service or replacement pricing is competitive. Our estimates are always firm with no hidden surprises. You can rely on C.M. Heating to advise you properly and to do excellent work promptly.
CM Heating performed a furnace maintenance and found furnace condensate trap is leaking. Condensate trap will need to be replaced. Part is covered under “Part Only Warranty”. Customer will be responsible for $291 dollars in Labor charges.
Tech found no other issues with furnace or ductless heating system. Both systems are running within factory specifications.
CM Heating Performed maintenance on a gas furnace. Check filter, clean cabinet check burner operation, check pilot operation, check inducer/blower operation, check safety components. Perform maintenance on a hot water heater, check inlet/outlet connection, check expansion tank, check thermostat operation, check thermal expansion valve, flush tank. System operating normally.
CM Heating performed a furnace and hot water tank maintenance and found Ducts have never been cleaned
Blower is clean
Inducer is quiet
Heat exchangers ok
Warranty is voided due to age
Filter clean upon arrival
Drip leg on Gas line is present
Flex is present
Surge protector is missing
No access for duct cleaning
Minimum filtration at furnace
Missing air purifier
Ignitor is in range
Unit is up there in age guessing about 18
Whole home air purifier
And replacement next failure.
Overall unit is in good running condition at this time. However at this age it is out of manufactures warranty and is no longer very efficient. Estimated 62% efficient at this time. Replace for more efficient unit with new warranties.