If your gas furnace in Edmonds, WA is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Edmonds, WA. C.M. Heating has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on C.M. Heating to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
We provide gas furnace service in Edmonds, WA
We provide gas furnace repair in Edmonds, WA
95% Gas Furnace
Performed hot water tank and furnace maintenance. All major electrical components passed. Furnace passed all checks. Recommended a new filter within the next two months. Fan motor blades dirty.
Drained 5 gallons from hot water tank. Noted a small leak from ontake valve shut off. Advised client to watch it and call the office if it gets worse.
Customer Stated That Her System Would Not Heat. Upon Arrival, The Technician Found That The Batteries Had Been Knocked Out Of Place.
CM Heating Performed A Diagnostic Service On The Gas Furnace Determined The Nest Thermostat Was Not Fully Wired Correctly For The Furnace. Made Rewired Corrections For Proper Operations.
Conducted A Maintenance Inspection Of Both The Water Tank And Gas Furnace.
Water Tank Should Be Replaced Immediately And Gas Furnace At Minimum Next Year.
All Operations Normal At This Time.
Found Failed Blower Motor And Other Repairs Needed Sold Replacement Equipment Being Installed On Tuesday
Returned And Replaced Pressure Switch. Cycled And Tested Furnace. Verified Flame Safeties And Temp Rise. System Running Well At This Time.
Upon Arrival Found System With 2 Flash. Error Code Indicating Unresponsive Pressure Switch. Tested Pressure Switch And It Is Not Closing When Venting Is -1.51” Of Draft And Pressure Switch Is Rated At -.55”. Tried To Order OEM Pressure Switch From Thrifty Supply But Their Covid Hours Are 7-11, And I Was And Hour Late. Will Order Part Tomorrow And Schedule A Return Trip.