Furnace Repair in Edmonds, Washington
Is your heating system not working, or perhaps behaving a little differently? Have you noticed that your home in Edmonds, WA is not maintaining temperature properly and making funny noises?
If your gas furnace is not working call C.M. Heating now. We fix broken heating equipment all the time in Edmonds, WA. Or if your system is just getting old, or giving you reasons not to trust it any more let us know. We have many years of experience and we can help you make the right choices when it comes to your furnace system.
CM Heating performed Maintenance on gas furnace, tested motors and capacitors, inspected electrical components and gas valve, tested co levels system is running normal at this time
CM Heating performed a furnace diagnostic and Tech found no signal being sent from thermostat to furnace. Tech found call for heat, but furnace would not kick on. Tech found thermostat not connected all the way to the back plate. Tech re secured thermostat to wall and furnace was able to fire on and off with no issues. Furnace was cycled several times.
CM Heating performed Maintenance on air handler and heat pump, tested motors and compressor, tested capacitors, inspected electrical components added an air scrubber and changed the filter, system is running normal at this time
CM Heating performed Maintenance on gas furnace, found burnt control board, leaking blower motor, failing inducer motor, and high co levels and had to shut down furnace
CM Heating Completed furnace maintenance. Furnace has extensive rust under inducer motor. And throughout furnace cab. Inducer also makes a loud squeal on startup although the noise is inconsistent it indicates that the bearings are shot and the inducer needs to be replaced. Due to age of unit and condition of furnace I cannot recommend replacement or repairs. I recommend replacement of furnace.
CM Heating Performed gas furnace maintenance. Check safety devices, performance components, and verified proper operations of the unit.
Filters changed, checked sensors, and consumable components for out of range tolerance.
Vacuumed dust out of the unit.
All operations normal at this time.