Air Conditioning Service, Repair and Installation Everett, Washington
C.M. Heating is one of the leading providers of air conditioning repair and air conditioning service in Everett, WA, offering timely solutions to problems related to your air conditioning system. Our HVAC technicians will come to your rescue when you want emergency AC service or repair, or just need a hand with your residential or commercial cooling problems.
You'll find we take our job seriously and highly value the trust that is placed in us. C.M. Heating goes far beyond what others do by investing in the training and equipment necessary to protect your home or family in Everett, WA.
Whether you have a central AC system, Heat Pump or Ductless Mini Split we are here to help.
CM Heating Performed a preventive maintenance service on Gas Furnace, hot water tank, and heat pump.
-Checked and ensure all safety components are within manufacturers requirements and working properly.
-Measured -/+ tolerance on consumable components.
-Inspected mechanical and electrical devices/parts within the unit.
-Refrigerant pressure verified.
-Inspected tank for leaks and flush the system. Tank does not have an expansion tank.
All operations normal at this time.
CM Heating Perform maintenance on a gas furnace, ac, hot water heater. All system operating normally.
CM Heating performed maintenance on furnace (GF), Hot water Tank (HWT), and Heat pump/Air conditioner (HP/AC).
GF Maintenance - System is running well, all components are within manufacturer’s specifications and in good working order. EAC has been pulled and cleaned, furnace vacuumed. No issues at this time.
HWT Maintenance - Tank has been flushed and inspected for any leaks (gas/water). All in good working order, no issues.
HP/AC Maintenance - All components are within manufacturer’s specifications and are in good working condition. Tested only in heat mode due to temperature outside but performance in heating is great. No issues at this time.
CM Heating performed prepaid maintenance's on the fireplace, furnace and AC units in home. Customer on monthly gfp and heat and cool clubs.
Fireplace in good working condition. Cleaned and tested
Furnace in good working condition. Cleaned tested. Filter.
Ac working well at this time. Amp draws and dual cap good. Everything clean and working properly.
Customer says that their air conditioner was not cooling, they thought maybe it needed refrigerant. Upon diagnosis the technician found a leak in the coil system.
CM Heating Performed maintenance on ac system.
CM Heating performed Maintenance on gas furnace, air conditioner and water heater, tested capacitors, inspected electrical components and motors, tested compressor, replaced filter, system is running normal at this time
CM Heating performed a maintenance on a furnace and air conditioner. Furnace and air conditioner working properly at this time. Checked all amp readings, and electrical componets. All capacitors in range and refrigerant levels normal. Getting proper temp rise and drop.
Furnace has dirty blower wheel and blower motor is leaking oil. Recommend clean blower wheel, and potential replacement of blower motor.
Air scrubber will help filter catch more dust/purify air/protect system.
Hot water tank flushed, purged of air and tested. Unit operating properly.
CM Heating performed an Air conditioning diagnostic and Found ac wiring on control board not wired correctly reset wiring and system is running at this time
CM Heating Performed maintenance on AC unit. Check safety circuits, performance of consumable components, refrigerant level/pressure, and the proper operations of the AC unit. Measurable specifications are all within manufacture design.
All operations normal at this time.
CM Heating performed an air conditioner diagnostic and found crossed wires on thermostat to control board. As well as performed a routine maintenance on the unit, tested capacitor and compressor and fan motor. We Cleaned inside and out and tested temperature drop and system is running at this time.
CM heated performed a maintenance on an AC and gas Furnace. Tune and clean gas furnace. Removed and cleaned the burners and flame sensor. Tested the capacitor, gas pressure and igniter. Took amp draws of motors. Visually inspected the control board and blower assembly. Cleaned filters and checked delta t.
Inducer motor house is cracked. Igniter is testing high resistance.
Tune and clean ac. Tested capacitor, contactor, pressures, delta t and amp draws.
System is running at this time. Recommend replacing furnace due to age. Recommend changing filter to 4in paper pleat due to dust getting past the current filter.
CM Heating Completed maintenance on furnace, ac and tankless. All units operating properly at this time. No concerns. Added air scrubber.