Furnace Cleaning Everett, Washington
Keeping your heating system in Everett, WA in good working order working requires scheduled maintenance. All equipment manufacturers suggest at least annual system cleaning and preventative maintenance. Our heating service technicians have years of experience working on furnaces like yours in Everett, WA. C.M. Heating service vehicles are on call 24 hours per day are fully equipped with the tools and parts necessary to keep your hot air furnace in good working order.
Our furnace repair, furnace service or replacement pricing is competitive. Our estimates are always firm with no hidden surprises. You can rely on C.M. Heating to advise you properly and to do excellent work promptly.
CM Heating performed a furnace maintenance and found all operations normal. Flame sensor was reading low but is back to above range. Replaced failed run cap. Cl and full cabinet and circuit board. Igniter was within range. Tested system from thermostat with no issues.
CM Heating performed furnace Maintenance - System is running well, all components are within manufacturer’s specifications. Output at nearest vent is over 100 degrees, all operations normal. No issues at this time, recommend annual maintenance.
CM Heating performed furnace maintenance, found unit working properly. Cleaned all components, and tested unit.
CM Heating Performed gas furnace maintenance. Check safety devices, performance components, and verified proper operations of the unit.
Filters changed, checked sensors, co2 levels, and consumable components for out of range tolerance.
Blower motor has moderate to heavy dirt build up but due to long term build condition it may have an adverse effect if clean. Would not recommend cleaning, a better solution would to replace the motor when it fails with a new motor.
Hot water tank has not signs of leakage, clean flush, and working properly.
CM Heating Perform gas furnace maintenance, service burner assembly, service flame sensor.
Detected small gas leak from shut off valve to unit.
Inspect gas pipe thread/re-seal and tighten. No leak detected.
CM Heating performed furnace maintenance and found all furnace operations normal. Flame sensor within range, spark igniter and variable speed motor. Cleaned full cabinet and circuit board. Tested system from thermostat with no issues. Hot water tank flushed and verified no leaks. Filled tank and relit pilot light.
CM Heating performed a furnace maintenance and found all Furnace operations normal. Flame sensor, igniter all within range. Cleaned full cabinet and circuit board. Replaced filter. Customer has variable speed motor that makes a rough start up sound but sounds fine after running and does not make harsh sound when ramping down. Notified customer that the noise on start up is normal.
CM Heating Performed maintenance service on gas furnace and heat pump unit. All equipment is working as design and properly per manufacturers specification. Installed air scrubber air purification system within the heating & cooling equipment and new 4’’ air filter.
All operations normal at this time.
CM Heating Completed furnace maintenance. No concerns at this time. Replaced Thermostat.