Furnace Repair in Everett, Washington
Is your heating system not working, or perhaps behaving a little differently? Have you noticed that your home in Everett, WA is not maintaining temperature properly and making funny noises?
If your gas furnace is not working call C.M. Heating now. We fix broken heating equipment all the time in Everett, WA. Or if your system is just getting old, or giving you reasons not to trust it any more let us know. We have many years of experience and we can help you make the right choices when it comes to your furnace system.
CM Heating Found the gas valve bad. The part is under warranty, need to order part and return for repair.
Replace Gas Valve under Parts Warranty
Customer stated their blower fan is consistently running. She has had the furnace off all summer and just fired it up and it will just blow consistently. Upon investigation, the technician found that the damper control was sending 24V to G terminal while switched off. This indicates a stuck closed relay. I disconnected it and tested the unit. Due to age of unit, I would recommend upgrading to a more efficient model.
Customer called requesting standard maintenance on their gas furnace and their tankless water system. System is running well, all components are within manufacturers specifications. No issues other than thermostat which home owner is aware of. Recommend annual maintenance
Tankless Maint - Unit has been flushed and inspected. All operations normal at this time.
Customer would like to have her furnace maintained before winter. She would also like her blower wheel and assembly cleaned. System was operational upon arrival. I checked the components within the unit and found the blower capacitor was out of specifications. It was replaced with new one. Blower assembly was pretty dirty. I cleaned the assembly. Burner assembly was ok, I cleaned flame rod. CO output was nominal. Heat output was also nominal. No other issues at this time.
CM Heating performed an electric furnace Diagnostic - Upon investigation, I found that the sequencer has failed which is why all heat elements are not being activated (3 out of 5 work). This is the second replacement sequencer needed in less than 5 years of operation, the unit is an old model of air handler and only source of heat. Replacement of sequencer is needed, however, based on age and efficiency recommend upgrade of system.
CM Heating went out for a gas furnace diagnostic and Found the igniter bad, 20 year. Old furnace recommend a consultation. If the customer decides to go ahead with the repair we would need to order the igniter from Lennox.
CM Heating went out for a gas furnace diagnostic and found pressure valve is open and wont turn on furnace; customer did not want universal pressure switch as recommended
CM Heating performed a Gas Furnace Diagnostic. Customer wanted his echo bee thermastat installed that he had bought himself. Furnace was working fine just wanted his thermastat installed. He thought that the $99 service fee was going to cover that but explained to him what the service fee was for, and explained that there is a additional install fee for the stat. Customer didn’t want to pay the additional fee so I called the office had them listen to the call to make sure we explained to the customer correctly and to see how they would like me to proceed. So I quoted the customer the fee to install the thermostat but he didn’t want us to install it so I left.
CM Heating went out for a Furnace diagnostic and Found the Igniter cracked replaced and tested. Service call and igniter to be reimbursed upon new Furnace install.
CM heating Performed diagnostic on gas furnace bad flame sensor quote replacement homeowner went forward with repair. Replace failed flame sensor with new furnace fired right up. Inducer motor struggling and is pulling high amp draws leaving quote to replace. All operations normal at this time.