Gas Fireplace, Gas Logs Service Everett, Washington
C.M. Heating offers full repair and maintenance services for hearth products in Everett, WA. If you have a dv gas fireplace, fireplace insert, gas stove, or gas logs, our service technicians have the experience to keep your system operating safely and at peak efficiency.
C.M. Heating stocks the parts and has the experience necessary to keep your gas fired fireplace or stove running properly.
CM Heating preformed a fireplace maintenance per customer contract.
CM Heating Completed gas fireplace maintenance, found batteries in place as alternate source of power. They should not be installed when unit is plugged in, only when power is out.
Customer would like to have their GF maintained, there are no concerns with the GF at this time.
Customer would also like to have their GFP maintained & diagnosed.
Customer stated that their GFP shuts off at random while they are running the unit, and also stated that the pilot will go out at random as well.
Customer would like to have the GFP checked out, and both units maintained.
No further concerns at this time.
Customer stated the pilot light keeps going out on their gas fireplace. They haven't had the unit serviced in a couple of years. Upon arrival, the technician found that the unit had a faulty redundant switch. After removing that and cleaning all other components of the unit, they found that it was operating properly.
CM Heating Cleaned and inspected fireplace. Tested Thermopile, it has good voltage. Unit was functioning normally while I was there. Possible causes: wall switch or failing valve. Recommend replacing wall switch before valve.
CM Heating Cleaned and inspected gas fireplace unit. Did not find anything wrong with unit mechanically. Spoke with tech support, they want to see Duracell or Energizer batteries in unit because of high battery power demand upon startup. Advised customer of this. Also, I relocated receiver antenna to improve communication with transmitter.
CM Heating went out for a gas fireplace diagnostic and found Gas valve stuck open after lighting, recommend replacing valve/pilot or replacing unit.
CM heating went out for a fireplace diagnostic and found Unit has bad gas valve. Highly recommend replace unit, 20 yers old. Consult set for 11/23 @10-1
CM Heating Cleaned and inspected gas fireplace. Unit is functioning normally at this time.
CM Heating went out for a fireplace diagnostic and a furnace inspection per contract.