Heat Pump Cleaning Everett, Washington
Annual maintenance of heat pump and air conditioning and heat pump systems is critical to maintain efficient reliable equipment performance. C.M. Heating can service all types of heat pumps in Everett, WA. Our service technicians can completely clean and service your HVAC systems in Everett, WA to give you the peace of mind that your system will perform well for months to come.
If you need system repair, C.M. Heating stocks the heat pump parts parts you need. If you need to update your AC or Heat Pump system in Everett, WA, we install a range of replacement systems.
CM Heating Performed maintenance on a HP, EF, and Hot water heater.
CM Heating performed a heat pump and ac maintenance and found Both systems working as well as they can, no issues found on maintenance.
CM Heating Performed a routine preventive maintenance service on the comfort heat pump equipment.
-Checked and ensure all safety components are within manufacturers requirements and working properly.
-Measured -/+ tolerance on consumable components.
-Inspected mechanical and electrical devices/parts within the unit.
At this time all operations are normal.
The following is my recommendations/findings that should be addressed:
-Heat pump coil is dirty, recommend a coil cleaning.
CM Heating performed a ductless heat pump maintenance and inspected all units for leaks, filter condition (filters cleaned and paper filters checked), performance (supply temperature) and coils cleaned. Outdoor unit has been cleaned and connections inspected. All operations normal at this time, no issues.
CM Heating Performed maintenance on heat pump system, check filter, safety components operation, refrigerant pressure/levels. All system operating normally.
CM Heating performed a Maintenance on ductless system. Cleaned head unit, filters, and outdoor unit. Checked voltage and delt t. System is running properly at this time
CM Heating performed a ductless heat pump maintenance and found Upon arrival, front cover was removed.
Cleaned indoor coil, outdoor coil. Wiped off units, added condensate tabs. Customer had already cleaned filters. Ductless system is carrier, 4 years old. Customer states there is a drain issue, but explained that due to age of unit and not installing, we are unable to help at this time.
CM Heating Tuned and cleaned air handler and heat pump. System running properly at this time
CM Heating Cleaned ductless unit inside and out, outdoor coil, and indoor coil, added condensate tab, cleaned filters, wiped down both units, changed batteries. Unit in good working condition. Inspected all components. No concerns at this time.
CM Heating performed a ductless and furnace maintenance and found Furnace in good working condition. No issues. Cleaned filters
Ductless units maintained. Coils cleaned, batteries replaced, unit wiped down, condensate tabs added, no issues.