Heat Pump Cleaning Everett, Washington
Annual maintenance of heat pump and air conditioning and heat pump systems is critical to maintain efficient reliable equipment performance. C.M. Heating can service all types of heat pumps in Everett, WA. Our service technicians can completely clean and service your HVAC systems in Everett, WA to give you the peace of mind that your system will perform well for months to come.
If you need system repair, C.M. Heating stocks the heat pump parts parts you need. If you need to update your AC or Heat Pump system in Everett, WA, we install a range of replacement systems.
CM Heating Performed maintenance on a ductless heat pump system. Clean filter, clean indoor unit, clean coil, check discharge/intake temperature, clean outdoor coil, check safety components. System operating normally.
CM Heating Performed maintenance on AH and HP system, check filter, check blower operation, check indoor coil, check condensation pump/drain, check safety components. Perform maintenance on tankless water heater, clean intake filter, check for leaks, check flame sensor/igniter, flush tankless. Perform maintenance on a gas fireplace. Clean glass, vacuum clean cabinet, check burner pan, check firebox, check thermopile, check gas valve, check safety components. All system operating normally.
CM Heating Performed maintenance on AH/HP system. Clean filter, check indoor coil condition, check blower operation, check auxiliary heat operation, check safety components, check capacitor, check contactor, check temp split. System operating normally.
CM Heating performed maintenance on a gas fireplace and heat pump per customer request.
CM Heating performed an Air handler and heat pump maintenance complete. No concerns, cooling properly. Filter changed, checked all electrical components and refrigerant levels.
CM Heating performed a ductless maintenance and cleaned Indoor head units. Wiped, coil clean, condensate tabs added. Outdoor coil cleaned, was heavily impacted with cotton/debris. Unit clean and in proper working condition.
CM Heating performed Maintenance on ductless system. Cleaned all head units and filters. Checked delta t, wiring and voltages. System is running properly at this time
CM Heating performed a heat pump maintenance:
Blower wheel is clean
Indoor coil is clean
Capacitor is in range
Surge protector is missing on heat pump
Hard start kit out of spec range
Outdoor coil is getting cotton wood build and should be cleaned for max efficiency
Tested system, changed filter 16x20x1, updated sticker, all operations are normal at this time.
CM Heating Performed maintenance on ductless heat pump unit. Checked electrical safety circuits, condition of evaporator and condenser coils, fan blade and wheel, drain lines, and fins.
Cleaned unit and filters. Checked remote operations, installed anti-fungus strips and treated the coils with mold control. Will schedule a return visit to replace thermostat once it arrives.
CM Heating Performed a routine maintenance service on the heat pump unit. Visit 2 of 2 was completed today.
Changed out batteries of the thermostat on this visit. Checked the condition of the filter, capacitor, Refrigerant pressures and electrical connections.
All parts and operations within manufacturers specifications at this time.
CM Heating Performed maintenance on a ductless heat pump system. Clean indoor unit filter, condition coil, clean cabinet, check for leaks, check condensation drain, check discharge/intake temperature, check outdoor unit operation, check disconnect, check safety components, clean outdoor unit. System operating normally.
CM Heating Performed maintenance on heat pump unit. Check safety circuits, performance components, refrigerant level/pressure, and the proper operations of the heat pump.
The unit is 20 years old and has reach manufactures design life expectancy. The system is showing signs of wear and is still functional but it’s advisable to replace the system due to significant wear to refrigerant tubing, motors, and electrical insulation which has the potential of unexpected failure.
CM Heating Performed a heat pump maintenance service.
-Took measurements of consumable components and verify they are within specific tolerance.
-Compared baseline refrigerant data to current readings.
-Inspect electrical and mechanical components for premature wear/failure.
-Inspect overall operations.
-Changed out dirty filter for new temporary 1 inch filter. Recommend using the correct size of 16x20x4.
All comfort equipment are operating well within design perimeters at this time.
Performed comprehensive coil cleaning service due to excessive dirt/dust within the outdoor coils. This service will help maintain peak air flow performance of the outdoor coil system.
CM Heating performed a ductless diagnostic and Cleared drain and poured 8 glasses of water down the drain to actuate the pump. Cleaned off the indoor coil and cleaned the filters. If this continues to leak there could be a slight crack in the drain pan. The customer will monitor.