Heat Pump Cleaning Everett, Washington
Annual maintenance of heat pump and air conditioning and heat pump systems is critical to maintain efficient reliable equipment performance. C.M. Heating can service all types of heat pumps in Everett, WA. Our service technicians can completely clean and service your HVAC systems in Everett, WA to give you the peace of mind that your system will perform well for months to come.
If you need system repair, C.M. Heating stocks the heat pump parts parts you need. If you need to update your AC or Heat Pump system in Everett, WA, we install a range of replacement systems.
CM Heating performed a ductless heat pump maintenance and found Upon arrival, front cover was removed.
Cleaned indoor coil, outdoor coil. Wiped off units, added condensate tabs. Customer had already cleaned filters. Ductless system is carrier, 4 years old. Customer states there is a drain issue, but explained that due to age of unit and not installing, we are unable to help at this time.
CM Heating performed a Maintenance on ductless system. Cleaned head unit, filters, and outdoor unit. Checked voltage and delt t. System is running properly at this time
CM Heating Performed maintenance on heat pump system, check filter, safety components operation, refrigerant pressure/levels. All system operating normally.
CM Heating Cleaned ductless unit inside and out, outdoor coil, and indoor coil, added condensate tab, cleaned filters, wiped down both units, changed batteries. Unit in good working condition. Inspected all components. No concerns at this time.
CM Heating performed a ductless and furnace maintenance and found Furnace in good working condition. No issues. Cleaned filters
Ductless units maintained. Coils cleaned, batteries replaced, unit wiped down, condensate tabs added, no issues.
CM Heating Performed maintenance on a ductless heat pump system. Clean filter, clean indoor unit, clean coil, check discharge/intake temperature, clean outdoor coil, check safety components. System operating normally.
CM Heating performed maintenance on a gas fireplace and heat pump per customer request.
CM Heating Performed maintenance on AH and HP system, check filter, check blower operation, check indoor coil, check condensation pump/drain, check safety components. Perform maintenance on tankless water heater, clean intake filter, check for leaks, check flame sensor/igniter, flush tankless. Perform maintenance on a gas fireplace. Clean glass, vacuum clean cabinet, check burner pan, check firebox, check thermopile, check gas valve, check safety components. All system operating normally.
CM Heating Performed maintenance on AH/HP system. Clean filter, check indoor coil condition, check blower operation, check auxiliary heat operation, check safety components, check capacitor, check contactor, check temp split. System operating normally.
CM Heating performed a heat pump maintenance:
Blower wheel is clean
Indoor coil is clean
Capacitor is in range
Surge protector is missing on heat pump
Hard start kit out of spec range
Outdoor coil is getting cotton wood build and should be cleaned for max efficiency
Tested system, changed filter 16x20x1, updated sticker, all operations are normal at this time.
CM Heating performed Maintenance on ductless system. Cleaned all head units and filters. Checked delta t, wiring and voltages. System is running properly at this time
CM Heating performed a ductless maintenance and cleaned Indoor head units. Wiped, coil clean, condensate tabs added. Outdoor coil cleaned, was heavily impacted with cotton/debris. Unit clean and in proper working condition.
CM Heating performed an Air handler and heat pump maintenance complete. No concerns, cooling properly. Filter changed, checked all electrical components and refrigerant levels.