Heat Pump Service Everett, Washington
C.M. Heating services all types air conditioners or heat pumps in Everett, WA. Our service technicians can diagnosis and repair your packaged or split systems in Everett, WA and get your HVAC system back up to speed promptly.
Let us help you decide how best to solve you comfort and efficiency challenges quickly. If repair is the best choice, C.M. Heating stocks the parts you need. If you need to update your AC or Heat Pump system in Everett, WA, we install a range of replacement systems.
CM heating performed a heat pump Diagnostic - Upon investigation, I found that the thermostat was not properly set for current equipment. The previous repairs of the replacement of the defrost board and outdoor sensor are still operational, I did move the sensor to the outside of the unit to better detect ambient air. I adjusted the following in the thermostat settings; 0170, 0350, and 0360. All of which have to do with current system set up. Tested unit in all operations, average temperature from supply vents is 97 degrees. All operations are normal at this time, recommend annual maintenance.
CM heating performed a heat pump diagnostic and Needed to reconnect the outdoor temperature sensor to the thermostat.
CM heating Performed maintenance on heat pump air hander unit. Check safety circuits, performance components, refrigerant level/pressure, and the proper operations of the unit. Install new air filter.
All operations normal at this time.
Customer recently purchased home and stated that the air wasn't very cold. Upon testing heat pump diagnostic determine refrigerant level was low about 16.4 oz. Performed electronic leak test no leaks were found, recharged system to manufacture specs. Due to system running low on refrigerant there could be possibilities that other components may have damage- the indoor unit TXV may have a restriction, the unit is not performing optimal at the moment. Due to age, unknown low refrigerant conditions and system running on low refrigerant recommend new unit or TXV replacement.
Customer's HP is leaking. CM Heating installed a HP, had to uninstall it for some pre-existing water damage to be repaired, then we had to re-install the unit.
Now, the unit is leaking and causing the customer's laminate floors to buckle. Our technician found Re-piped condensate drain lines due to a leak in the piping connection. After completion performed a leak test. No farther leaks from condensate piping.
Recommend a water detection alarm.
All operations normal at this time.
Customer stated that their heat pump was not working. Our technician found that the heat pump was not running upon arrival. I checked the components and found the contactor was fried. I replaced contactor and system started up. Cooling was running nominal. Heating does have an issue. There appears to be icing up after the service valve in liquid line. Pressures are reading low, there may be a restriction in the threaded adapter to the service valve (cannot repair today, would need to quote replacement). No other issues.
CM Heating performed a heat pump diagnostic and Did not find the root of the problem. There are a couple possibilities of current issues creating the problem after long run times. Need to order a condenser fan motor and a replacement filter. Honeywell accordion style 20x20.
CM Heating performed a heat pump diagnostic and Found the capacitor blown, removed and replaced ran and tested. Recommend High Efficient gas furnace and Air Conditioner upon replacement of system.
CM Heating performed a Diagnostic on air handler and heat pump. ON ARRIVAL FOUND RESIDENT HAD OPENED EQUIPMENT TO SELF DIAGNOSE. TSTAT IS HANGING OFF THE WALL.
Found no low voltage. popped fuse is most likely from the thermostat not being properly mounted and knicks in the thermostat wires. Replaced the fuse and was able to test system in emergency heat, cooling and heating.
System has 16 degrees delta t in cooling. Heat has 5 degrees delta t. Refrigerant pressure and visual frosting of the liquid line shows blockage at the external piston.
Recommend replacing unit due to age and costs for repairs. Comfort advisor scheduled for 5/9/19 10-12 arrival
CM Heating performed a heat pump diagnostic and Found refrigerant line broken near repair from last November will get technician to return to repair asap
CM Heating performed a diakin ductless heat pump diagnostic and found Freezing conditions cause fan to seize up by ice. Cleared free the fan and tested the unit, all operations normal at this.
CM Heating performed a heat pump diagnostic and Found the system working as well as it can. Do to the age of the equipment I recommend replacing the system with a more efficient quieter system. I also recommend the disconnect be raised up to a higher location upon new install. Reimburse the service call upon install.