Heat Pump Service Everett, Washington
C.M. Heating services all types air conditioners or heat pumps in Everett, WA. Our service technicians can diagnosis and repair your packaged or split systems in Everett, WA and get your HVAC system back up to speed promptly.
Let us help you decide how best to solve you comfort and efficiency challenges quickly. If repair is the best choice, C.M. Heating stocks the parts you need. If you need to update your AC or Heat Pump system in Everett, WA, we install a range of replacement systems.
CM Heating performed a heat pump diagnostic and Found refrigerant line broken near repair from last November will get technician to return to repair asap
CM Heating Performed a diagnostic service on heat pump unit. Fan had stop working, no amps with a bad capacitor. Replaced with new and test the system. All operations normal at this time.
CM Heating performed a Diagnostic on air handler and heat pump. ON ARRIVAL FOUND RESIDENT HAD OPENED EQUIPMENT TO SELF DIAGNOSE. TSTAT IS HANGING OFF THE WALL.
Found no low voltage. popped fuse is most likely from the thermostat not being properly mounted and knicks in the thermostat wires. Replaced the fuse and was able to test system in emergency heat, cooling and heating.
System has 16 degrees delta t in cooling. Heat has 5 degrees delta t. Refrigerant pressure and visual frosting of the liquid line shows blockage at the external piston.
Recommend replacing unit due to age and costs for repairs. Comfort advisor scheduled for 5/9/19 10-12 arrival
CM Heating performed a heat pump diagnostic and Found the system working as well as it can. Do to the age of the equipment I recommend replacing the system with a more efficient quieter system. I also recommend the disconnect be raised up to a higher location upon new install. Reimburse the service call upon install.
CM Heating performed a heat pump diagnostic and Did not find the root of the problem. There are a couple possibilities of current issues creating the problem after long run times. Need to order a condenser fan motor and a replacement filter. Honeywell accordion style 20x20.
CM Heating performed a heat pump diagnostic and Found the capacitor blown, removed and replaced ran and tested. Recommend High Efficient gas furnace and Air Conditioner upon replacement of system.
CM Heating completed a service on both heat pump and air handler. Tech replaced Contactor in heat pump, because original had burn marks on both contacts to the point where it would soon affect operation. Tech replaced batteries in thermostat and OD sensor for customer. System is in good working order..
CM Heating performed a heat pump diagnostic and Tech found failed run capacitor. Tech replaced capacitor and was able to fire system off with no issues.
CM Heating performed a heat pump diagnostic and Replaced lithium batteries in outdoor temperature sensor. Quick visual check of the heat pump system.
Dirty filter, recommend replacing approximately every 8-12 months also recommend an annual maintenance plan. Please see attached estimate.
CM Heating Performed a diagnostic service on ductless heat pump head unit. Fixed leaking pan and performed a deep cleaning service.
Also, completed a maintenance on both the outside and inside units.
All operations normal at this time.