Heat Pump Service Everett, Washington
C.M. Heating services all types air conditioners or heat pumps in Everett, WA. Our service technicians can diagnosis and repair your packaged or split systems in Everett, WA and get your HVAC system back up to speed promptly.
Let us help you decide how best to solve you comfort and efficiency challenges quickly. If repair is the best choice, C.M. Heating stocks the parts you need. If you need to update your AC or Heat Pump system in Everett, WA, we install a range of replacement systems.
CM Heating Performed maintenance on a gas furnace/Heat Pump. Upon arrival customer stated the system is not blowing air thru the vents. After inspection found the blower motor is out of commission, check other system components to ensure proper diagnosis. Found multiple issues with indoor/outdoor unit. Unit is 10-12 years old and has not been serviced since install. Customer has been setup for a new equipment consultation for furnace/Hp November 8th 10-12 pm. System is powered down to prevent damage/ safety purposes.
CM Heating performed a heat pump diagnostic and Tech found failed run capacitor. Tech replaced capacitor and was able to fire system off with no issues.
CM Heating completed a service on both heat pump and air handler. Tech replaced Contactor in heat pump, because original had burn marks on both contacts to the point where it would soon affect operation. Tech replaced batteries in thermostat and OD sensor for customer. System is in good working order..
CM Heating Performed a heating and cooling maintenance service on the air handler-heatpump unit.
-Took measurements of consumable components and verify they are within specific tolerance.
-Compared baseline refrigerant data to current readings.
-Inspect electrical and mechanical components for premature wear/failure.
-Inspect overall operations.
-Install new 4in media air filter.
All comfort equipment are operating well within design perimeters at this time
CM Heating went out for a heat pump diagnostic and found No power running to heat pump. Re set breakers and checked disconnect. Customer will need to contact an electrician to repair voltage issue.
CM Heating performed a heat pump and furnace maintenance per customer request.
CM Heating performed a heat pump diagnostic and Found and repaired some wires on the contactor, system is running normal at this time)