Installed new furnace.
Customer was unable to get the filter box open. We found no issues with how the filter box was installed, the door panel is just difficult to pull off. We were able to show the customer a way to get it open.
Thermostat says the outdoor sensor requires new batteries. Customer is unable to change batteries die to health restrictions. We were unable to get them into emergency heat because the indoor unit would not come on. We installed new lithium batteries in the outdoor sensor.
Coleman TG9S060A10MP11 95% Gas Furnace
Replaced 25 year old furnace with new down flow Colman 80% natural gas 60,000 BTU furnace with 10 year parts and labor warranty per quote.
We performed a pellet stove diagnostic. We cleaned and inspected unit, tested for proper operation and the unit was working properly. Customer needs to replace thermostat with a proper thermostat, customer says they will replace.
Technician removed old 80% gas furnace and replaced with a new unit.
Installation of 2 head ductless system, including all materials, electrical, labor, permits, and equipment.
Bradford White RE340S6
Install new 40 Gallon Bradford White Hot Water Tank, including earthquake straps, expansion tank, stand, and permits
Installation of a Coleman AC/Coil and GF
Customer had Goodman Gas Furnace installed.
American Standard HVAC 4A7A3030 Split Air Conditioner
Installed a Gas Furnace and Air Conditioner.
We installed a single head Daikin LV 24,000 BTU LV 24,000 BTU MINI SEER 2.0 Tons Single Zone Wall Mount Mini Split
Customer stated that they have no heat, no ignition. We replaced the fail hot surface igniter.
We installed a new Daikin 19 Series 18,000 BTU Single Head system.