Tankless Water Heater Service Everett, Washington
Tankless hot water heaters are excellent prodocts in Everett, WA! But what do you do when they are not meeting your expectations?
Answer: you call C.M. Heating. We are extremely well equipped, stocked, and trained to solve your tankless hot water heating frustrations and keep your system in peak working order. C.M. Heating are the top tankless water heater professionals in Everett, WA. We've seen the successes of tankless & solved the frustrations of customers who have endured the service of less qualified companies. We service, repair & provide warranty services on all tankless brands of tankless hot water heaters.
Call C.M. Heating to get the most of your tankless water heating system.
Technician Completed duct cleaning, gfp maintenance and gf maint.
Technician performed an maintenance on a tankless and gas furnace.
Customer's tankless hot water heater is leaking. Condensate pump for water heater was cracked and was leaking on the floor before or filled up and drained. I replaced the condensate pump. Back flushed tank. Pulled inducer and cleaned. Tested all functions and all operations are within manufactures specs.
CM heating performed tankless water heater maintenance and found Tankless water heater all operations normal. Flushed tank and cleaned sensors and cabinet. Cleared air bubbles and vinegar from pipes. Furnace all operations normal. Flame sensor and igniter within range. Run cap for fan motor out of range. Left message with property management for replacement.
CM heating performed a Tankless Diagnostic - Upon investigation, I found that the water leak was coming from the inducer housing but has been dried up without any new water spots. Water leak was small amount of water to begin with. Since no new water marks are visible, test ran unit to spot check, we will pay more attention to area moving forward and if leak is still present we can apply silicone to area or replace housing.
and a Gas Furnace Maintenance - System is running well, all components are within manufacturer’s specifications. EAC cells have been cleaned, unit vacuumed and test ran unit to ensure it is fully operational. No issues at this time.
CM Heating performed Tankless Maintenance - Unit has been flushed and inspected for any leaks. All components are in working order. No issues at this time.
CM Heating Performed gas furnace and tankless maintenance. Check safety devices, performance components, and verified proper operations of the unit.
Filters changed, checked sensors, co2 levels, and consumable components for out of range tolerance. All operations and parts within manufacture requirements.
CM heating Flushed tankless. Cleaned cabinet and sensors. Inspected inducer system and burners with no issues. Cleared filter at faucet to speed up hot water to bathroom and kitchen.
1. Performed gas furnace maintenance. Check safety devices, performance components, and verified proper operations of the unit.
Filter changed out, checked/clean sensors. All operations within manufacture requirements.
2. Tankless unit flushed, checked components, and tested operations. All operations normal at this time.