Water Heater Service and Repair Everett, Washington
C.M. Heating services and repairs all types of water heaters in Everett, WA. We specialize in tank and tankless hot water heaters. Our service technicians can diagnosis and repair your electric or gas water heaters promptly. We offer same day water heater service in Everett, WA.
Let us help you decide how best to solve your water heating problems. If repair is the best choice, C.M. Heating stocks the parts you need. If you need a new water heater in Everett, WA, we install a range of water heating systems.
CM Heating performed a water heater diagnostic and found the hot water tank pilot light would not stay triggered because of bad thermocouple. Replaced thermocouple and pilot stayed lit and main burners ignited with no issues.
CM Heating performed a hot water tank diagnostic and the Hot water tank fired up first try. Explained to customer that pilot light needs to build up charge with the flame before it stays lit. Customer states no reason for pilot to go out, asked customer to catch error code if problem happens again.
CM heating Performed a furnace maintenance operated the system to ensure proper operation, also hot water tank inspection. No issues found.
CM Heating performed hot water tank diagnostic and found Thermostat control for the upper element is not working properly. Will need to contact Bradford white to see how to proceed since the unit is under warranty still, but unsure if warranty is transferable to the new homeowner. The office will contact the customer with information regarding the hot water tank and warranty.
CM Heating Inspected water heater and determined that venting seems to be correct and to code. Tank is 15 years old and is leaking, due to lack of service and acidic sediment build up inside tank. Customer would like a quote on a new tank.
CM Heating performed a water tank diagnostic and Recommend replacing the expansion tank. The customer would like to move forward with the repair.
CM Heating performed a Maintenance on gas furnace and water heater, pulled and cleaned burners and flame sensor, replaced igniter, tested motors and capacitor, tested gas pressure, drained and inspected water heater, system is running at this time, recommend pulling blower motor and cleaning along with adding an air scrubber plus to protect system better
CM Heating performed Maintenance on Hot Water Tank and furnace.
Removed and cleaned the burners and flame sensor. Tested the Igniter, carbon monoxide levels, and delta t. There is metal flashing obstructing the capacitor. Unable to test. Took amp draws of motors. Visually inspected the control board and blower assembly.
Blower assembly has significant dust accumulation after the filter. There is a hole cut into the installation and duct work allowing dust/dirt past the filter. The control board has burn marks on the back. Hot surface Igniter is turning white with age.
***no guarantee on functionality of equipment without repairs or replacement.
Recommend replacing the equipment due to age and accumulating cost of repairs.
CM Heating Performed a gas furnace and hot water tank maintenance service. Conduct a inspection of water and gas lines for leaks. Check the condition of burners- The furnace burner has some rust build up.
Ensured safety devices are working as design within the furnace. Consumable components are within specifications per manufacture.
Flush sediments from hot water tank.
All operations normal at this time.
CM Heating Completed hot water tank and furnace maintenance. Hot water tank is fairly new and functioning properly.
Furnace is in good working condition however due to its age I would recommend replacement of entire unit instead of replacing any major components that may fail in the future.
CM Heating performed a water tank maintenance. Tune and clean gas furnace. Cleaned burners and flame sensor. Tested the gas pressure and igniter. Took amp draws of the blower motor and inducer motor. Visually inspected the control board and blower assembly. Checked filter. Furnace is running properly at this time. Recommend upgrading the air filter system to air Scrubber