Furnace Repair in Lake stevens, Washington
Is your heating system not working, or perhaps behaving a little differently? Have you noticed that your home in Lake stevens, WA is not maintaining temperature properly and making funny noises?
If your gas furnace is not working call C.M. Heating now. We fix broken heating equipment all the time in Lake stevens, WA. Or if your system is just getting old, or giving you reasons not to trust it any more let us know. We have many years of experience and we can help you make the right choices when it comes to your furnace system.
Customer stated that the gas furnace was not coming on but not producing heat. During investigation of unit, discovered HSI was reading high on resistance. Blower wheel is dirty and should have cleaning at next visit. Blower capacitor was out of manufacturer's specifications. Gas valve has leak at the inlet. All of these will require attention.
Lake Stevens, WA
We installed a gas furnace in customer's home in 2016 and they noticed a water trail coming from the furnace, The customer was unable to determine where the leak was coming from. Upon investigation, the technician found a leak where the exhaust pipe comes out of the furnace. Glue broke loose from the connection and when we had the heavy rains it was leaking onto the top of the furnace and down the intake side and into the furnace. I put silicone on the area where the glue had broke loose to seal any openings. Tested furnace from thermostat and did not find any other issues. Furnace was installed in 2016. I recommend annual maintenance to ensure proper operations and longevity of the equipment.
Lake Stevens, WA