No Heat in Lynnwood, Washington
Furnaces can be intimidating especially when they're not working. However there might be a silver lining to this stressful situation: roughly a quarter of all service calls can be resolved with easy fixes that are simple and inexpensive.
At C.M. Heating we help homeowners like you in Lynnwood, WA all the time with their heating systems. From simply offering advise, to complete system replacement, we have the knowledge and experience to help you resolve the challenges your heating system is presenting in the best possible way.
CM Heating performed a furnace diagnostic and Added a 1 inch filter holder and air scrubber. Also pull and clean blower wheel.
Immediate issue was inducer motor cycling. After adjusting wiring, this problem was solved.
CM Heating found all furnace operations normal on arrival. Customer says furnace will blow cold air randomly and not operate in heat just started two days ago. Pilot assembly and burners had build up of dust and it was affecting sensors. Cleaned burners. Capacitor for blower motor was reading low and out of range, replaced capacitor. Cleaned furnace and all operations normal.
CM Heating Performed diagnostic on gas furnace had loud buzzing transformer (see pictures for details) added anti vibration pad under transformer cut noise in half maybe but customer could still hear it in the bedroom. Replacing part under parts warranty per quote. All operations normal at this time.