Furnace Service and Repair Marysville, Washington
If your gas furnace in Marysville, WA is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Marysville, WA. C.M. Heating has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on C.M. Heating to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
We provide gas furnace service in Marysville, WA
We provide gas furnace repair in Marysville, WA
CM Heating Performed Maintenance on gas furnace. System is running upon arrival. Tested and inspected all major components. Per homeowner approval, cleaned blower assembly and replaced capacitor. Installed 4 inch filter. All systems are running at this time.
Recommend replacing filter every 4-6 months.
NOTE: WE WILL NEED TO RETURN IN SPRING/SUMMER TO HONOR AC VISIT. IT WAS TOO COLD TO PERFORM AC MAINTENANCE TODAY.
CM Heating Performed a diagnostic service on gas furnace found the control board has failed/damage due to improper nest thermostat installation. Coleman voids all warranty due to customer or any non professional installation.
Part has been ordered and office will schedule a return visit for repairs.
Non-operational at this time.
CM Heating went out for a furnace diagnostic but The gas furnace was working as normal when I activated the unit upon arrival. Inspected the components for any abnormalities. Found condensation trap either clogged or leaking. Rust bellow the area.
Operations normal at this time.
CM Heating performed Maintenance on furnace. Checked burners and flame sensor. Tested capacitors. Visually inspected the control board and blower assembly. Took amp draws of motors. Changed filter.
Furnace is running properly at this time
Maintenance on heat pump. Checked delta t. Took amp draws of compressor and fan. Tested capacitor, contactor and defrost board.
System is running properly at this time
CM Heating performed a furnace diagnostic and Found and replaced failed capacitor and system is running normal at this time recommend getting quotes for new equipment due to age