Heat Pump Service Marysville, Washington
C.M. Heating services all types air conditioners or heat pumps in Marysville, WA. Our service technicians can diagnosis and repair your packaged or split systems in Marysville, WA and get your HVAC system back up to speed promptly.
Let us help you decide how best to solve you comfort and efficiency challenges quickly. If repair is the best choice, C.M. Heating stocks the parts you need. If you need to update your AC or Heat Pump system in Marysville, WA, we install a range of replacement systems.
CM Heating performed a heat pump diagnostic and Replaced faulty transformer with new and installed new batteries into thermostat. Assisted customer with programming the thermostat. All operations normal at this time.
CM Heating performed a diagnostic on a ductless heat pump and Removed 8 ounces of refrigerant in the system. Pressurized with nitrogen and the system held 96psi for over 45 minutes, once beau brought out some nitrogen I pressurized the system to 315psi and it also held. Placed the system in a vacuum and the vacuum didn’t hold, added dye kit and 6.25lbs 410A. If the leak was caused by workmanship there is no cost for repair, however if the leak was caused by something else there will be a charge to repair it.
CM Heating performed a diagnostic on a heat pump unit and found The system is working as it should, the frost is normal and the system is defrosting. Recommend a late spring maintenance to check both AC and Heat. 100%
CM Heating performed Maintenance on heat pump. Checked delta t, capacitor, board and took amp draws of the compressor. Outdoor temp is 61 degrees and will not give accurate delta t or cooling pressures.
Heat pump is running at this time
Recommend adding surge protection to the heat pump to better protect the unit
As well as Tuned and cleaned gas furnace. Checked burners and flame sensor. Tested capacitor and gas pressure. Took amp draws of motors. Visually inspected the control board and blower assembly. Checked filter and delta t. Furnace is running properly at this time
CM Heating performed service on ductless system and water heater. Ductless system is in good working order. Tech found lots of sediment and debris in water heater. Tech flushed around 7-8 gallons of water and dark water filled with sediment was found in each bucket. Highly recommended that customer think about new unit. System is from 2002.
CM Heating Performed maintenance on ductless heat pump. Checked and/or clean air filters and cabinet housing as needed. Checked for loose electrical connections, and refrigerant leaks. Help customer setup thermostats.
All units are working properly.