Heat Pump Service Mountlake terrace, Washington
C.M. Heating services all types air conditioners or heat pumps in Mountlake terrace, WA. Our service technicians can diagnosis and repair your packaged or split systems in Mountlake terrace, WA and get your HVAC system back up to speed promptly.
Let us help you decide how best to solve you comfort and efficiency challenges quickly. If repair is the best choice, C.M. Heating stocks the parts you need. If you need to update your AC or Heat Pump system in Mountlake terrace, WA, we install a range of replacement systems.
CM Heating performed a diagnostic on heat pump. Error code on defrost board 7 flash LPC. Changed filter.
Outdoor temp is 59 degrees. Second stage cooling pressures 110/196.4 psi 16.2 SH/10.7 SC degrees. SLT 52.1/ LLT57 degrees held for 10 minutes.
Second stage heating pressures 119.2/300.3 psi 92.5 SH/ 13.1 sc degrees. SLT 132.9/ LLT 82.9 degrees held for 30 minutes as did not fault.
Heat pump is running at this time.
If problem persists please call. Recommend having Kevin assist.
Mountlake Terrace, WA