Furnace Cleaning Seattle, Washington
Keeping your heating system in Seattle, WA in good working order working requires scheduled maintenance. All equipment manufacturers suggest at least annual system cleaning and preventative maintenance. Our heating service technicians have years of experience working on furnaces like yours in Seattle, WA. C.M. Heating service vehicles are on call and are fully equipped with the tools and parts necessary to keep your hot air furnace in good working order.
Our furnace repair, furnace service or replacement pricing is competitive. Our estimates are always firm with no hidden surprises. You can rely on C.M. Heating to advise you properly and to do excellent work promptly.
CM Heating Performed gas furnace maintenance. Check safety devices, performance components, and verified proper operations of the unit.
Checked sensors, air flow, and consumable components for out of range tolerance.
Checked tankless water heater for leaks, condition of burners, mineral sediment, and flushed the system. All operations and parts within manufacture requirements.
Recommend adding an electronic air cleaner to help supplement the 1in filter style.
CM Heating Performed a heating maintenance service on the gas furnace.
-Took measurements of consumable components and verify they are within specific tolerance.
-Ensure all safety devices are in proper working order.
-Inspect electrical and mechanical components for premature wear/failure.
-Conducted a CO2 reading, performance temperatures, inspected for gas leaks and/or carbon.
-Inspect overall operations.
-Replaced filter with new.
-Vacuumed carbon dust from cabinet.
1. 13 year old system has some light noise resonating from the inducer motor may indicate bearing wear or excessive carbon residue built up.
2. Blower motor has excessive dirt/dust build up. Air filter extremely dirty. Last changed 8/2017.
3. Excessive carbon dust- Mostly due to system running with restricted air flow. Abnormal air/fuel ratio.
4. Sparked and flame sensor showing some wear. 13 years old original components.
5. No gas line drip leg.