Furnace Service and Repair Snohomish, Washington
If your gas furnace in Snohomish, WA is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Snohomish, WA. C.M. Heating has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on C.M. Heating to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
We provide gas furnace service in Snohomish, WA
We provide gas furnace repair in Snohomish, WA
CM Heating Performed a diagnostic on the gas fireplace and gas furnace. Gave customer $29 off gas furnace service fee.
1. Gas fireplace gas valve had failed. Thermo sensors has some wear.
2. Gas furnace capacitor had failed.
1. Replaced and installed new gas valve only. Advised customer of pilot components I recommend replacing before failure.
2. Replaced and installed new capacitor. Performed amp draws of motor and corrected air filter.
Completed a maintenance service the gas fireplace. All operations normal for both the fireplace and furnace.
CM Heating went out for a furnace and heat pump maintenance and found Furnace is around 15 years old. Past it’s average life expectancy, but is overall in good shape. I found no issues with mechanical components at this time.
Service on water heater was completed. Water heater is in good working order. Around 5 gallons was flushed from system. Burner and pilot assembly are in good shape. Unit has a recirculating pump, that is not plumbed in. Customer should contact plumber to pipe in pump.
I found no issues with heat pump. Unit has a proper charge, and all components are running within factory specifications.
CM Heating went out for a furnace diagnostic but found no issues with system. Signed customer up for membership but no additional charge for the trip.
CM Heating went out for a furnace diagnostic for customer but Could not duplicate fault system is running at the time of arrival. No charge for visit, will return if problem persists.