If your gas furnace in Snohomish, WA is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Snohomish, WA. C.M. Heating has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on C.M. Heating to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
We provide gas furnace service in Snohomish, WA
We provide gas furnace repair in Snohomish, WA
Variable Speed Gas Furnace
Inspected the system. Found the power switch was turned off when the hot water tank was replaced. Turned the switch on and the system is now running. I recommend yearly service on the furnace and ac
Tune And Clean On The Gas Furnace. Pulled And Cleaned The Burners And Flame Sensor. Checked The Temp Rose, Amp Draw And Gas Pressure. The Inducer Motor Is Louder Than Normal. The Blower Motor Is Leaking Oil And The Blower Wheel Is Dirty. The Gas Flex Line Runs Through The Cabinet. The System Is Running At This Time. I Recommend Replacing The Furnace Due To The Age And Cost Of Recommended Repairs. Customer Is Going To Call In And Schedule And Estimate For Replacing The Furnace And Possibly Adding Ac.
Completed Furnace Diagnostic, Discovered That The Gas Had Been Turned Off At The Furnace. Once I Turned The Gas On The Furnace Worked However Th Hot Surface Igniter Is Going Bad, Readings Show The Resistance Is 162+ Anything Over 100 Is Considered Failed. My Other Concern Is The Age Of The Furnace, The Average Lifespan Of A Furnace Is Around 15 To 20 Years, The Reason Being Is All Of The Parts Are Aging At A Similar Rate And Tend To Fail Back To Back. Usually It's Cheaper In The Long Run To Replace The Entire Furnace Instead Of Perpetually Replacing Parts. Found A Manufacturer Date Of 1997.
Replaced Intermittently Operating Azon1050 With New AZON1050. After Programming And Inspection Of System Found Air Scrubber Bulb Failed. Need To Return With Xformer And Ozone Free Bulb, Ordered For Tuesday Delivery From Gensco