Heat Pump Cleaning Snohomish, Washington
Annual maintenance of heat pump and air conditioning and heat pump systems is critical to maintain efficient reliable equipment performance. C.M. Heating can service all types of heat pumps in Snohomish, WA. Our service technicians can completely clean and service your HVAC systems in Snohomish, WA to give you the peace of mind that your system will perform well for months to come.
If you need system repair, C.M. Heating stocks the heat pump parts parts you need. If you need to update your AC or Heat Pump system in Snohomish, WA, we install a range of replacement systems.
CM Heating performed a heat pump maintenance and found the heat pump low on refrigerant added 3 lbs and the system was responding well, there is a leak in the system. With the age of the equipment I recommend replacing vs repairing do to the cost of a leak check.
CM Heating performed an Air handler, Heat pump and water heater maintenance.
HP/AH Maintenance - System is running well (tested in heating and cooling), all components have been inspected and are within manufacturer’s specifications. The condensate trap at the furnace was a little bit clogged which can lead to water pooling in evaporator pan. I cleared out trap and poured water in the line to ensure proper drainage but I recommend installing a clear condensate trap with safety switch to prevent any damage to coil in the event there is backed up water in the system. Filter has been replaced with a 1’ filter as part of maintenance but recommend replacing with 4’ filter. No other issues at this time, recommend annual maintenance!
HWT Maintenance (Garage) - Tank has been flushed and inspected for leaks. Elements are in good working condition and expansion tank is good. No issues at this time.
CM Heating Performed maintenance on wall mounted ductless mini split. Cleaned filter replace remote batteries with new. Added anti microbial capsule in condensation pan. Cleaned indoor coil with no rinse coil cleaner. Out door units coil was very dirty and restricting air flow. Wash the coil spray with cleaner and rinsed. All operations normal at this time.
CM Heating performed 1st year maintenance on air handler and heat pump, cleaned inside and out, tested capacitor and compressor, tested motors, tested system in heating and cooling, system is running normal at this time