Heat Pump Service Snohomish, Washington
C.M. Heating services all types air conditioners or heat pumps in Snohomish, WA. Our service technicians can diagnosis and repair your packaged or split systems in Snohomish, WA and get your HVAC system back up to speed promptly.
Let us help you decide how best to solve you comfort and efficiency challenges quickly. If repair is the best choice, C.M. Heating stocks the parts you need. If you need to update your AC or Heat Pump system in Snohomish, WA, we install a range of replacement systems.
CM Heating performed a heat pump diagnostic and found The unit TXV is functioning, the defrost controller is working correctly. The heat pump is not performing at peak operations.
System measurements indicate a dirty or plugged condenser and over charged system.
Recommendation as follow:
1. Evaporator coil cleaning.
2. Condenser coil cleaning.
3. Refrigerant recovery and re-charge.
CM Heating performed Maintenance on air handler and heat pump. Took amp draws of compressor, motors and heat strips. Visually inspected the control board and blower assembly and coil. Checked delta t and filter. Tested capacitor and defrost mode.
System is running properly at this time
CM Heating performed a Diagnostic on air handler and heat pump. Thermostat shows fault code 126 equipment loss. This is most likely the result of power fluctuations due to weather. Equipment is running properly at this time
Added 3 surge protectors to air handler and heat pump to protect and warranty the system. Power surges are considered “act of god” and void standard equipment warranty.
CM Heating performed a heat pump diagnostic and Found failed outdoor unit set up install for monday morning 7-9 arriva
CM Heating performed a heat pump diagnostic and found System was tripped on a hard lock out. I could not find what caused the system to lockout. Inverter system was tested in all phases and could not get system to trip again. Possible power spikes may have caused issue with heat pump. If issues continue, field manager to return with tech for further diagnostic.
CM Heating went out for a heat pump diagnostic and Upon inspection found the issue is related to previous visit and set fee was removed. The issue with the system is intermittent only in heating cycle. Spoke with tech support and its determined that the indoor coil is not compatible with the outdoor units capacity. Need to come back with matching coil to complete repair.