C.M. Heating services all types air conditioners or heat pumps in Snohomish, WA. Our service technicians can diagnosis and repair your packaged or split systems in Snohomish, WA and get your HVAC system back up to speed promptly.
Let us help you decide how best to solve you comfort and efficiency challenges quickly. If repair is the best choice, C.M. Heating stocks the parts you need. If you need to update your AC or Heat Pump system in Snohomish, WA, we install a range of replacement systems.
I found a leak on liquid line where filter dryer is located. I quoted customer for repairs. He is contacting original install company to make repair because it is a craftsmanship issue.
Diagnostic On Heat Pump. System Running On Arrival. Paul Reported The System Is Icing Over Really Bad. Found The Delta T At 14 Degrees And Refrigerant Pressures Are Under Charged. The Compressor Amps Are Fluctuating Between 6.5 Amp And 10.82 Amps. The Contactor Is Pitted And Should Be Replaced.
The System Is Running R22 Refrigerant Which Is No Longer Made. The Repairs Will Be Very Expensive And High Likelihood Of Other Issues With The System If Repaired.
Recommended Replacing Equipment
CM Heating Performed Maintenance On A Air Handler And Heat Pump System. Completed Full System Maintenance And Safety Inspection. All Operation Normal At This Time. See Inspection Report For Details.
CM Heating Performed A Maintenance On Air Handler And Heat Pump, Water Heater, Gas Fireplace. All System Operating Normally, Completed Maintenance And Safety Inspection. Customer Declined Renew At This Time Due To Potential Relocation Due To Work. See Inspection Report For Details.
CM Heating Performed A Maintenance Service On The Gas Furnace-heat Pump, And Fireplace. Checked System Components, Safety Devices, And Ensures Proper Operations.
Cleaned The Fireplace Unit Glass Of Carbon Deposits.
All Operations Normal At This Time.
CM Heating Performed A Heat Pump Diagnostic And Found Failed Outdoor Unit Set Up Install For Monday Morning 7-9 Arriva
CM Heating Performed A Diagnostic On Air Handler And Heat Pump. Thermostat Shows Fault Code 126 Equipment Loss. This Is Most Likely The Result Of Power Fluctuations Due To Weather. Equipment Is Running Properly At This Time
Added 3 Surge Protectors To Air Handler And Heat Pump To Protect And Warranty The System. Power Surges Are Considered “act Of God” And Void Standard Equipment Warranty.