No Heat in Stanwood, Washington
Furnaces can be intimidating especially when they're not working. However there might be a silver lining to this stressful situation: roughly a quarter of all service calls can be resolved with easy fixes that are simple and inexpensive.
At C.M. Heating we help homeowners like you in Stanwood, WA all the time with their heating systems. From simply offering advise, to complete system replacement, we have the knowledge and experience to help you resolve the challenges your heating system is presenting in the best possible way.
CM Heating performed Maintenance on 24 year old weather king furnace. System is running upon arrival. Tested and inspected all major components.
Found some parts that are showing signs of age and potential failure. Found blower assembly pretty dirty and electronic air cleaner not working. Appears the power head has failed. Recommended switching to 4 inch paper filters (20x25x4) instead.
Homeowner opted to have blower assembly pulled and cleaned and have paper filter installed. Recommend replacing filters every 4 months.
Furnace is heating at this time, but due to age, I would consider starting to look into replacement options for the future.