Furnace Service and Repair Bothell, Washington
If your heating system in Bothell, WA is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Bothell, WA. C.M. Heating has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on C.M. Heating to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
Maintenance on customer's Electric Furnace.
Customer stated that their gas furnace is cycling but not igniting and not producing heat. Upon diagnosis the technician found a failed hot surface igniter. The igniter was replaced and the unit is now working properly.
Customer states that their furnace isn't working properly. She says that currently it is producing heat but it doesn't always come on as it is supposed to. This may be as simple as a thermostat issue. Gas furnace is not functioning properly sometimes will not heat. Upon arrival I experienced the error code 2 green LED which is stuck open pressure switch. I checked pressure switch and it was functioning fine. I checked the amp draw of the inducer motor which turned out to be out of the manufacturer’s specifications. I also climbed onto the roof to ensure no blockage in the exhaust vent. When the furnace would start up the gas valve would actuate multiple times before actually relasing the NG. This may be a Gas valve issue or a control board issue. Owner has informed me that she would like to proceed with a free consultation due to the age of the unit and amount of potential repairs. There is also corrosion and water damage on the HE and burners. No other issues at this time.