Furnace Repair in Snohomish, Washington
Is your heating system not working, or perhaps behaving a little differently? Have you noticed that your home in Snohomish, WA is not maintaining temperature properly and making funny noises?
If your gas furnace is not working call C.M. Heating now. We fix broken heating equipment all the time in Snohomish, WA. Or if your system is just getting old, or giving you reasons not to trust it any more let us know. We have many years of experience and we can help you make the right choices when it comes to your furnace system.
CM Heating came out and performed a full maintenance on both of the customer's Electric Furnace / Air Handler units. No concerns at this time.
Customer requested maintenance for their electric furnace before listing their home for sale. He mentioned that the unit had not been turned on in awhile. Upon arrival, the technician found that they were unable to perform the standard maintenance because the furnace would not turn on. After performing a diagnostic, the technician jumped R and W terminals and EF started up (problem is with Thermostat). Thermostat was replaced and system is functioning properly. They found no other issues.
Customer had their blower motor on their gas furnace replaced in 2016, and the customer states now that it is not working--blower will not turn on, and will not run. Upon investigation, the technician found that the system was overcharged and EAC pre filters were clogged causing the suction line to freeze. I recovered about 3 ounces and got the suction line temp to increase, getting rid of icing issue. Output at vents is 50 degrees, Unit is fairly old and components are beginning to show signs of wear and age, recommend replacing versus repairing if any other issue occurs.
CM Heating came out and performed a diagnostic on this customer's Gas Furnace, and found that the thermostat was the issue.
We were able to get the thermostat working, however, we went ahead and replaced it with a new Honeywell T4 Thermostat
Customers igniter arced and was shorting plugged the molex conecter in better and it stopped shorting. Blower motor has high amp draws on worried its on its way out. But other wise all operations normal at this time. Set customer up with free equipment consultation and office is emailing quote for blower motor.